AAB841-S50 | Yokogawa Style S2 CENTUM VP ProSafe-RS Hybrid Analog I/O Module

2026-04-20T00:59:48-07:00

Type: Analog I/O Module
Price: 66.00

Product Overview

The Yokogawa AAB841-S50 (Style S2) serves as a versatile, high-density hybrid module for the CENTUM VP and ProSafe-RS FIO architectures. This module eliminates the need for separate input and output cards by offering 8 software-configurable channels. Each channel functions as either an Analog Input or an Analog Output, optimizing cabinet space in localized skid systems and integrated process control environments. We provide this unit as 100% brand new and original factory equipment to ensure maximum system availability.

Part Number Breakdown

The model code AAB841-S50 identifies the specific configuration for the FIO system:

AAB841: Hybrid Analog I/O Module (Input and Output capabilities).

-S: Standard type for standard signal environments.

5: Supports software-selectable AI/AO functionality across 8 channels.

0: Basic functional specification code.

Style S2: Latest hardware revision for improved thermal and electrical performance.

Technical Specifications

This module delivers high-speed signal processing with the following technical parameters:

Parameter | Specification
I/O Capacity | 8 Channels (Configurable as AI or AO)
Signal Range | 1–5 V DC
Accuracy | $\pm0.1\%$ of full scale for both AI and AO
Data Refresh Cycle | 10 ms per module
Input Impedance | $\ge 1$ MΩ
Output Load Resistance | $\ge 2$ kΩ
Temperature Range | -20°C to +70°C
Power Consumption | 450 mA typical (at 5 V DC internal bus)
Dimensions | 32.8 mm (W) × 130 mm (D) × 107.5 mm (H)

Engineering Advantages

Dynamic Channel Allocation: Software-selectable AI/AO channels allow engineers to adjust I/O counts without changing hardware. This flexibility solves the common problem of last-minute design changes on the plant floor, reducing spare part inventory.

Extreme Environmental Resilience: The wide operating temperature range (-20°C to +70°C) allows installation in non-climate-controlled field enclosures. This resilience makes the AAB841-S50 ideal for upstream oil and gas skids where ambient conditions fluctuate significantly.

High-Speed Loop Performance: A 10 ms data refresh cycle ensures near-instantaneous feedback for critical control loops. This speed enhances the precision of ProSafe-RS safety instrumented systems and CENTUM VP regulatory control.

Optimized Space Utilization: The compact 32.8 mm width packs 8 hybrid channels into a single slot. This high density directly reduces the physical footprint of the I/O rack, lowering the overall cost of control room cabinetry.

FAQs

Can I mix AI and AO channels on the same AAB841-S50 module?

Yes. You configure each of the 8 channels independently via the system software. This allows any combination of inputs and outputs within a single module.

Does this module support 4–20 mA current signals?

The AAB841-S50 operates on a 1–5 V DC signal range. To interface with 4–20 mA field devices, you must use a 250 Ω precision shunt resistor at the terminal board to convert the current signal to the required voltage.

What is the significance of the "Style S2" designation?

Style S2 represents an updated hardware revision. It maintains full backward compatibility with earlier styles but offers improved internal component heat dissipation and higher reliability in the extended temperature range.

Does the module provide per-channel galvanic isolation?

No. This module utilizes a shared-ground design (non-isolated between channels). It works best in applications where field devices share a common reference or where external isolation barriers already exist.